Commercial Condensers TC and TU series
Nominal capacities, taking into account Eurovent (EN327) standards,
condenser temperature Tc = 40 ° C, air inlet temperature Tai = 25 ° C, temperature difference
Δt = 15K and calculated for R404A gas at sea level.
Copper pipes Ø5 / 16 ”, Ø3 / 8”, Ø1 / 2 ”pipe thickness is 0.35 mm.
Fin material is aluminum, its thickness is 0.12 mm
• Lamella distance is 2.1 – 2.3 – 2.5mm,
• Input – output collector material is copper,
• Highest working pressure Ps = 33 Bar.
• Cassette is painted RAL 7044 on galvanized steel.
• Each fan section is separated from the other and reversed rotation of the standing fans.
its effect is prevented.
With refrigerants R404A, R507, R134A, R407C, R407, R22, R407A
suitable for work.